Vertical Exposed Type Fan Coil Unit
Use international brand or domestic high-quality brand HVAC dedicated inverter;
The use of frequency converters can effectively reduce energy consumption and operating costs;
Matching on the air handler can realize the variable air volume function;
Variable frequency starting can reduce the impact of starting current on the grid during starting, thereby reducing the cost of power capacity expansion;
Power supply, running status, fault status, remote/local status indication;
Automatic (remote) / manual (local) two control methods;
Overload, lack of phase, undervoltage and short circuit indications are perfect to realize comprehensive protection.
Cold Magic cabinet-type fan-coil air-conditioning unit consists of a filter, a high-efficiency heat exchanger, a low-noise fan, a frame and a panel. It is mainly used to process temperature and humidity and purify the air in the air-conditioning area. It is a central air-conditioning system. The main terminal equipment is widely used in hotels, theaters, shopping malls, hotels, office buildings and other occasions, and can meet the air-conditioning needs of various industries such as electronics, chemical fiber, textiles, cigarettes, pharmaceuticals, medical care, food, and light industry.
The ZK series air-conditioning unit is designed and manufactured by our company after years of research and development, using advanced technology to reduce noise and save energy. It brings together the advantages of similar products at home and abroad, with reasonable structure, beautiful appearance, superior performance, reliable quality, convenient disassembly and assembly, and long life. It is currently an advanced level of air-conditioning equipment at home and abroad.
Vertical series units are generally suitable for floor installation. Ceiling series units are generally used for ceiling installation and can be hidden in the ceiling. Horizontal series units can be installed on the floor or by hanging according to needs.
The working pressure on the water side of the cabinet air-conditioning unit can reach 1.6MPa.
Vertical surface mounted unit
This type of unit is suitable for direct arrangement in an air-conditioned room. There is a control switch on the unit, which can directly control the operation of the unit. It can also be equipped with frequency conversion speed control according to user needs.
•Use international brand or domestic high-quality brand HVAC dedicated inverter;
•The use of frequency converters can effectively reduce energy consumption and operating costs;
•Matching on the air handler can realize the function of variable air volume;
•Variable frequency starting can reduce the impact of starting current on the grid during starting, thereby reducing the cost of power •capacity expansion;
•Power supply, operating status, fault status, remote/local status indication;
•Automatic (remote) / manual (local) two control methods;
•Overload, lack of phase, undervoltage and short circuit indications are perfect to realize comprehensive protection.
Precautions for the installation and use of air conditioning units
1. When hoisting, the unit should be horizontally installed to ensure the removal of condensed water. After the unit is installed, the condensed water must flow toward the drain.
2. When installing on the ground, the unit should be placed on a cement boss with a certain height, and the boss plane should be flat and level.
The water seal position should be installed for the condensate discharge in the cold section of the surface.
3. Prevent debris from entering the fan impeller and motor during installation, and remove debris from the drip tray and condensate pipe before operation.
4. When the air pipe interface is not in line with the air outlet, the variable-diameter air pipe joint should be prepared on site, and the return air outlet filter should be cleaned regularly to prevent dust from clogging the coil fins and maintain the heat transfer effect of the coil.
5. The integrity of all parts should be checked before the equipment is installed, and damaged parts should be repaired in time.
6. The surface cooler and heater should be drained of internal water (gas accumulation) before use, and the unused surface cooler and heater should be drained in severe cold areas in winter (to prevent frost damage), and the heat and refrigerant must be treated Soften the water to reduce the scale in the pipe. After 2 to 3 years of use, the inner wall of the water pipe should be cleaned, and the scale should be removed by chemical descaling. The water pressure should be tested once a year (the pressure is 1.0MPa) to ensure that there is no leakage.
- Product serial number
- Name of product
- Product serial number:
- Vertical Exposed Type Fan Coil Unit
Add product X